The MRP-2002 is a six-zone FACP for single and dual hazard
agent releasing applications. The MRP-2002 provides reliable
fire detection, signaling and protection for commercial, industrial
and institutional buildings requiring agent-based releasing.
The MRP-2002 is compatible with System Sensor’s i3 detectors
which are conventional smoke detectors that can transmit
a maintenance trouble signal to the FACP indicating the need
for cleaning and a supervisory ‘freeze’ signal when the ambient
temperature falls below the detector rating of approximately
45°F (7.22°C). In addition, the control panel is
compatible with conventional input devices such as two-wire
smoke detectors, four-wire smoke detectors, pull stations,
waterflow devices, tamper switches and other normally-open
contact devices. Refer to the Fire•Lite Device Compatibility
Document for a complete listing of compatible devices.
Four outputs are programmable as NACs (Notification Appliance
Circuits) or releasing circuits. Three programmable
Form-C relays (factory programmed for Alarm, Trouble and
Supervisory) and 24 VDC special application resettable and
non-resettable power outputs are also included on the main
circuit board. The MRP-2002 supervises all wiring, AC voltage,
battery charger and battery level.
Activation of a compatible smoke detector or any normallyopen
fire alarm initiating device will activate audible and visual
signaling devices, illuminate an indicator, display alarm information
on the panel’s LCD, sound the piezo sounder at the
FACP, activate the FACP alarm relay and operate an optional
module used to notify a remote station or initiate an auxiliary
The MRP-2002E offers the same features as the MRP-2002
but allows connection to 220/240 VAC. Unless otherwise specified,
the information in this data sheet applies to both the 110/
120 VAC and 220/240 VAC versions of the panels.