Four outputs are programmable as NACs (Notification Appliance
Circuits) or releasing circuits. Three programmable
Form-C relays (factory programmed for Alarm, Trouble and
Supervisory) and 24 VDC special application resettable and
non-resettable power outputs are also included on the main
circuit board. The MRP-2001 supervises all wiring, AC voltage,
battery charger and battery level.
Activation of a compatible smoke detector or any normallyopen
fire alarm initiating device will activate audible and visual
signaling devices, illuminate an indicator, display alarm information
on the panels LCD, sound the piezo sounder at the
FACP, activate the FACP alarm relay and operate an optional
module used to notify a remote station or initiate an auxiliary
The MRP-2001E offers the same features as the MRP-2001
but allows connection to 240 VAC. Unless otherwise specified,
the information in this data sheet applies to both the 120 VAC
and 240 VAC versions of the panels.
Enter your email for a chance to WIN $100 Amex Gift Card.
Please Enter Your Email Address
*One entry per household please