Certification: UL Listed for USA and Canada
– Hazardous locations:
Class I, Div 2, Groups A-D. Class I, Zones 2
Class II, Div 2, Groups F & G.
Listing No: E186629
– Ordinary locations: Fire Alarm Box
Listing No. S8117.
California State Fire Marshal (CSFM) Listed
CSA Certified to C22.2 (PB only), Nos. 0-M, 0.4M, 14-M,
25,30-M, 94, 142-M 1987, 157M 1987, 157-92, Enclosure
Type 4, 4A, Class 1, Groups A-D, Cert. No. 79120.
ATEX Approved: EN50014, EN50018, EN50019,
EN50028. Cert. No. BAS02ATEX2105X (BG & PB), EExed
II C T6 (switch only), EExedm IIC T4 (other versions).
Voltage: Up to 240V.
Certified temp: BGUL: –13°F to +131°F (–25°C to + 55°C); PBUL: –13°F
+131°F (–25°C to +55°C). PB (CSA): -58°F to +104°F
(-50°C to +40°C).
Ingress Protection: NEMA 4x & 6, IP66 & 67.
Terminals: 6 x 14 AWG standard (BGUL), 7 or 9 x 14 AWG standard.
Switch Rating (1 or 2 changeover switches fitted): Max Rating 240VAC, 3A.
Cable Entries: Up to 4 entries 1⁄2” NPT.
Weight: 2.6 lb/1.2kg (Varies with model & entries).
Material: Glass reinforced polyester.
Finish: Red epoxy painted finish as standard or to Customer’s specification.
Resistors: Various configurations available on versions up to 24V, 470R minimum.
LED A high intensity red LED can be fitted as an optional extra to
Indication: indicate operation on versions up to 24V.
Labelling: BG Glass label – reads either
(1) Fire Break glass – press here.
(2) Break glass – press here.
(3) Worded to Client’s requirements.
PB & BG Duty label – worded to Client’s requirements. Riveted on.
PB & BG Tag label – worded to Client’s requirements. Screwed on.
Enter your email for a chance to WIN $100 Amex Gift Card.
Please Enter Your Email Address
*One entry per household please