The 2D51 photo electronic detector uses a state-of-the-art optical sensing chamber. This detector is designed to provide protection in duct applications when installed with an Innovair Flex 4-wire duct smoke detector housing and to be used with compatible UL listed control panels only. Two LEDs on each detector provide local visible alarm indication. They flash every five seconds indicating that power is applied and the detector is working properly. The LEDs latch on in alarm. LEDs will be off when a trouble condition exists indicating that the detector sensitivity is outside the listed limit. See applicable Innovair Flex duct smoke detector installation manual for more information.. The alarm can be reset by a momentary power interruption, test/ reset button, or remote test accessory with reset function. This detector may be tested by activating the internal reed switch with a magnet, test/ reset button, or remote test accessory.
Also known as
- System Sensor By Honeywell-Us 4-WIRE, PHOTO REPLACEMENT HEAD - BK-2D51